Oregon Roof Consulting - Roofing Hall of Shame - 2021
Here at ORC we are well into our ninth year of service, so we offer some more Hall Of Shame entries that are real doozies. Here we go!
New Roof Disaster-Lake Oswego, OR (Mar 28, 2021)
Just when we thought we had seen it all, we come across this nightmare. No contract (which is required by law and plus - it's typically a really good idea!); four different kind of rake metal profiles, which we found quite clever; two colors of step flashing, with many of them only 2" on the roof (the requirement is 5"); no starter shingles anywhere.... none; mangled and dented flashing everywhere; field shingle nails way too short; chimney flashing that looks like my rabbit did it; valleys done wrong. Here's the amusing part: this "contractor' actually said with a straight face he knew how to properly install a roof. Talk about egregious prevarication! Can you say FULL REFUND?
New Roof Inspection - SW Portland, OR (Mar 23, 2021)
The owners had what turned out to be valid concerns, so we went and had a look. They called Sunday morning at 11:00AM, I was there by 1:00PM, and they had their report by 6:00PM.
All shingle manufacturers put embossed nailing lines on their shingles. That is where the nail goes which is the strongest part of the shingle. This manufacture says "nails MUST be on this line". 90% were way above the line. It's just as easy to put a roof nail here as it is there. Proper fastening is crucial and is one of the most basic, fundamental, rudimentary aspects of roofing. It's actually quite simple and easy. I have actually done it - millions of times.
This contractor subs everything out, doesn't pay much, and charges very high prices. The only use one brand of shingles and have a sweetheart deal with that manufacturer. I have looked at about 14 of their roofs over the years and every one had significant legitimate issues. Many in the industry wish they would go away. The amount of bad reviews they have online is astounding and they just don't care.
New Roof Inspection - Happy Valley, OR (Mar 16, 2021)
What a mess. No text necessary here. These photos speak for themselves. Looks like my pet rabbit 'Missy' was up here doing this.........with apologies to 'The Hopper'.
Newer Roof Inspection - Salem, OR (Mar 04, 2021)
The owners had ventilation issues, so we drove down I-5 and had a look. The air intakes were blocked by insulation. Easy fix. The roof pretty much to industry standards. The nails for the ridge shingles too short but that's about it.
New Roof Inspection - Pacific City, OR (Mar 03, 2021)
The owner wanted an inspection of this new Malarkey Legacy roof before paying the bill. Lucky she did.
) Note the clever way the skylight was fastened - drive a large nail part way in then just bend it down with a hammer.
) Contract says 6 nails per shingle - there are 5 per shingle.
) Majority of nails under driven, over driven, angle driven.
) Underlayment under drip metal and on top of rake metal. Should be the opposite.
) 18 year El Cheapo pipe flashing on a 50 year roof.
) Ridge shingle nails too short.
) Toe board nails not banged down. Heads sticking up 1/4".
Owner will be demanding a full refund.
Roof Inspection - Lake Oswego, OR (Jan 19, 2021)
The owner had concerns about his new roof so we had a look. As always we check for proper fastening. With 11,000 nails on this roof some bad nails are to be expected however we discovered that over 90% of nails were way above the factory embossed nailing line with many over driven. This roof a Big Box job. All they do is find some hapless chump willing to work for $12 an hour up on a dangerous roof and tack on a large 'middle man' fee for the honor and priveledge of having them involved. How gracious of them! Every one of their roofs I have seen had multiple serious legitimate code issues. They are no longer dabbling roofing. The owner filed a warranty claim and will be getting a new roof. He was most pleased with our efforts.
Roof Repair Inspection - Sandy, OR (Jan 16, 2021)
After 'repair', this roof was still leaking so we had a look. The work didn't match up what the contract said - we see that a lot - so the owner found a real roofer that will come out and do it again, this time correctly. The amount of shoddy 'workmanship' we see on a regular basis is astounding! Certainly no shortage of incompetant ripoff cowboy roofers out yonder. Trouble is, they keep getting tangled up in their spurs.
New Roof Inspection - Rainier, OR (2021)
This was our second visit in three years. The previous roof was one of the worst we have seen so it was done again. Bad job so it will be done again. I felt sorry for the owner as he got screwed twice. Get this, the guy who did this roof was not a licensed roofer. He somehow got hold of a blank contract of some roofing company and filled it out and telling the owner he worked for that roofing company! What nerve! Talk about egregious prevarication!
Oregon Roof Consulting and Inspection Phone: (503) 654-4612 Cell: (503) 952-6479 Email:Visit our Contact page Mail: PO Box 220190, Milwaukie, OR 97222 OR CCB: 199121 WA License: OREGORC871MR
Residential and commercial roofing project consulting in Oregon; Portland Metro, Oregon; Bend, Oregon; Seattle, Washington; Washington State; and the Pacific Northwest area. Offering professional roof consulting, inspections, project monitoring, and certifications for property owners and homeowners.